|Categories||Carrier HVAC Manuals|
|Document Type||Heating, Ventilating and Air Conditioning Manual Free Download. HAVC Operator's Instruction Manual.|
|Product Brand||Carrier. Support Phone Number: In North America, please call 1-800-CARRIER for immediate customer assistance from 8:00a -5:00p (EST) weekdays , Heating, Ventilating and Air Conditioning - HVAC|
|Document File Type|
|Wikipedia's Page||Carrier Corporation|
Condensing Heat Exchanger Kit Cancels: IIK 340M-40-9 IIK 340M-40-19 6-96 Installation Instructions Part No. 320722-751, -752, -753, and -754 NOTE: Read the entire instruction manual before starting the installation. This symbol indicates a change since the last issue. KIT PART NO. Table 1–Kit Usage UNIT 340MAV 345MAV 350MAV 490AAV 024040 036040 024060 355MAV 58MCA 58MSA 58MXA 040-08 040-12 060-08 060-12 060-16 080-12 080-16 080-20 100-16 100-20 120-20 58MVP SAFETY CONSIDERATIONS Installing and servicing heating equipment can be hazardous due to gas and electrical components.
Only trained personnel should install or service heating equipment. Untrained personnel can perform basic maintenance functions such as cleaning and replacing filters. All other operations should be performed by trained service personnel. When working on heating equipment, observe precautions in the literature, on tags, and on labels attached to the unit. Follow all safety codes. Wear safety glasses and work gloves. Have a fire extinguisher available. Recognize safety information. This is the safety-alert symbol. When you see this symbol on the furnace and in instructions or manuals, be alert to the potential for personal injury. Understand the signal words DANGER, WARNING, and CAUTION. These words are used with the safety-alert symbol. DANGER identifies the most serious hazards which will result in severe personal injury or death. WARNING signifies a hazard which could result in personal injury or death. CAUTION is used to identify unsafe practices which would result in minor personal injury or product and property damage. 320722-751 042060 060-14 320722-752 320722-753 320722-754 042080 060080 060100 042040 060120 080-14 080-20 100-20 040-14 120-20 DESCRIPTION AND USAGE Use this condensing heat exchanger kit to replace a failed, factory-installed, condensing heat exchanger. This condensing heat exchanger kit contains the following items: Condensing heat exchanger assembly (includes collector box) Outlet cell panel gasket Outlet cell panel screw Installation Instructions INSTALLATION 1 1 7 maximum 1 Turn off gas and electrical supplies to unit before beginning any installation or modification. Follow operating instructions on label attached to furnace. Failure to follow this warning could result in personal injury or death. Step 1–Remove Whole Cell Panel Assembly See Fig. 1 for furnace component locations. See Fig. 2 for expanded view of heat system components. NOTE: Actual component location may vary depending on model and series. Label all wires prior to disconnection when servicing controls. Wiring errors can cause improper and dangerous operation. INTRODUCTION This instruction covers installation of the condensing heat exchanger kit Part No. 320722-751, -752, -753, and -754 in multipoise, 40-in. tall, condensing gas furnaces. 1. Turn off gas and electrical supplies to furnace. 2. Remove main furnace door. 3. Remove blower access panel. 4. Disconnect field power supply wires from J-box. 5. Remove 2 screws securing J-box.