|Categories||Carrier HVAC Manuals|
|Document Type||Heating, Ventilating and Air Conditioning Manual Free Download. HAVC Operator's Instruction Manual.|
|Product Brand||Carrier. Support Phone Number: In North America, please call 1-800-CARRIER for immediate customer assistance from 8:00a -5:00p (EST) weekdays , Heating, Ventilating and Air Conditioning - HVAC|
|Document File Type|
|Wikipedia's Page||Carrier Corporation|
ICM Inducer Motor Assembly Kit Cancels: IIK 355M-40-4 IIK 355M-40-5 8-96 Installation Instructions Part No. 320727-754 PRIMARY HEAT EXCHANGER (BEHIND CELL INLET PANEL) COMBUSTIONAIR INTAKE CONNECTION AUXILIARY JUNCTION BOX VENT OUTLET INDUCER MOTOR WIRE CONNECTOR CONDENSING HEAT EXCHANGER (BEHIND CELL INLET PANEL) INDUCER HOUSING DRAIN TUBE CONDENSATE TRAP AIR FILTER AND RETAINER NOTE: Read the entire instruction manual before starting the installation.
This symbol indicates a change since the last issue. SAFETY CONSIDERATIONS Installing and servicing of heating equipment can be hazardous due to gas and electrical components. Only trained personnel should install or service heating equipment. Untrained personnel can perform basic maintenance functions such as cleaning coils or cleaning and replacing filters. All other operations should be performed by trained service personnel. When working on heating equipment, observe precautions in the literature, on tags, and on labels attached to the unit. Follow all safety codes. Wear safety glasses and work gloves. Have fire extinguisher available. Recognize safety information. This is the safety-alert symbol. When you see this symbol on the furnace and in instructions or manuals, be alert to the potential for personal injury. Understand the signal word DANGER, WARNING, and CAUTION. These words are used with the safety-alert symbol. DANGER identifies the most serious hazards which will result in severe personal injury or death. WARNING signifies a hazard which could result in personal injury or death. CAUTION is used to identify unsafe practices which would result in minor personal injury or product and property damage. BURNER ENCLOSURE GAS VALVE CAP AND CLAMP (UNUSED DRAIN CONN.) INDUCER MOTOR VENT OUTLET PRESSURE SWITCHES CONTROL CENTER BLOWER ACCESS PANEL SAFETY INTERLOCK SWITCH MOTOR AND BLOWER ASSEMBLY A93407 NOTE: Actual component location may vary depending on model and series. Fig. 1–Inducer Motor Assembly in Upflow Furnace Orientation Before beginning any installation or modification, be sure the main electrical disconnect switch is in the OFF position. Electrical shock can cause personal injury or death. NOTE: Inducer assembly consists of motor, wheel, motor mount, motor weight, inducer cover, inducer housing, vent cap, and vent clamp. INSTALLATION Step 1–Remove Old Motor Assembly 1. Turn electrical supply to unit to OFF position. 2. Remove main furnace door. 3. Remove lower drain tube from inducer housing cover. 4. Remove pressure switch assembly by removing 2 screws. (See Fig. 1.) 5. Remove pressure switch tube at tee leading to burner box and gas valve. 6. Move pressure switch assembly to side.