|Categories||Carrier HVAC Manuals|
|Document Type||Heating, Ventilating and Air Conditioning Manual Free Download. HAVC Operator's Instruction Manual.|
|Product Brand||Carrier. Support Phone Number: In North America, please call 1-800-CARRIER for immediate customer assistance from 8:00a -5:00p (EST) weekdays , Heating, Ventilating and Air Conditioning - HVAC|
|Document File Type|
|Wikipedia's Page||Carrier Corporation|
Furnace Control Relocation Kit Cancels: New IIK 340M-40-37 8-97 Installation Instructions Part No. 320393-751 NOTE: Read the entire instruction manual before starting the installation. SAFETY CONSIDERATIONS Installing and servicing heating equipment can be hazardous due to gas and electrical components. Only trained and qualified personnel should install, repair, or service heating equipment. Untrained personnel can perform basic maintenance functions such as cleaning and replacing air filters.
All other operations must be performed by trained service personnel. When working on heating equipment, observe precautions in the literature, on tags, and on labels attached to or shipped with the unit and other safety precautions that may apply. Recognize safety information. This is the safety-alert symbol. When you see this symbol on the unit and in instructions or manuals, be alert to the potential for personal injury. Understand the signal words DANGER, WARNING, and CAUTION. These words are used with the safety-alert symbol. DANGER identifies the most serious hazards which will result in severe personal injury or death. WARNING signifies a hazard which could result in personal injury or death. CAUTION is used to identify unsafe practices which would result in minor personal injury or product and property damage. NOTE is used to highlight suggestions which will result in enhanced installation, reliability, or operation. INTRODUCTION This kit is to be used to replace and relocate the control center on all (Series A or 101) 40-in. fixed capacity multipoise condensing furnaces from the controls compartment to the blower compartment regardless of furnace installed orientation. Installing and servicing heating equipment can be hazardous due to gas and electrical components. This conversion kit is to be installed by a qualified service agency in accordance with the manufacturer’s instructions and all applicable codes and requirements of the authority having jurisdiction. If the information in these instructions is not followed exactly, a fire or explosion may result causing property damage, personal injury, or loss of life. The qualified service agency performing this work assumes responsibility for the proper conversion of this furnace with this kit. ELECTROSTATIC DISCHARGE (ESD) PRECAUTIONS Electrostatic discharge can affect electronic components. Take precautions during furnace installation and servicing to protect the furnace electronic control. Precautions will prevent electrostatic discharges from personnel and hand tools which are held during the procedure. These precautions will help to avoid exposing the control to electrostatic discharge by putting the furnace, the control, and the person at the same electrostatic potential. 1. Disconnect all power to furnace. DO NOT TOUCH THE CONTROL OR ANY WIRE CONNECTED TO THE CONTROL PRIOR TO DISCHARGING YOUR BODY’S ELECTROSTATIC CHARGE TO GROUND. 2. Firmly touch a clean, unpainted, metal surface of the furnace chassis which is close to the control. Tools held in a person’s hand during grounding will be satisfactorily discharged. Table 1–Kit Contents PART DESCRIPTION Fixed Capacity Control and Bracket Assy Flame Sensor Harness Blower Shelf Bracket Service Label Caution Label Conversion Label Installation Instructions Screw (8A x 1/2 in.) Hex Head Rollout Switch Wire Tie Plug Button Grommet Harness Retainer Wiring Label PART NO. 324179-701 322219-301 322220-201 324173-101 322255-101 324174-101 IIK340M-40-37/58M-52SI FAW5808B HH18HA252 HY76TB125 KA51AD403 KA56GR140 AS86BL032 322854-101 QTY 1 2 1 2 1 Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice and without incurring obligations.